Installation services for Sealings
Due to the increasing complexity of technical building equipment, choosing the right sealing system is not always easy. Not only the different pipe and cable systems, but also the installation distances and component thicknesses make it difficult to select a fire barrier that complies with the approval.
A YouTube video is embedded here. This content is not displayed due to your lack of consent to third-party content.
For pipe seals, the Model Building Regulation stipulates that pipelines may only be passed through space-enclosing components with the prescribed fire resistance if the fire has not spread for a sufficiently long time or if precautions have been taken.
As a precaution, pipe seals are used that either have the same fire resistance as the room-enclosing components or go beyond that. They must be made of non-combustible building materials. More details are specified in the German "Muster-Leitungsanlagen-Richtlinie" (MLAR) (model pipe system guidelines).</p
The regulations for buildings in building classes 1 and 2 or within flats and within the same utilisation unit with up to 400 m² on up to two floors are less strict. There is also relaxation for individual electrical lines, more precisely specified pipelines made of selected, non-flammable building materials up to 160 mm outside diameter and installation pipes for electrical lines up to 32 mm outside diameter made of flammable building materials, aluminium or glass.
Pipe seals are primarily required for pipes that can burn or melt, such as plastic pipes. Although the fire can spread further inside the pipe, further spread is prevented at the openings, for example by means of fire protective collars as fire-retarding sealings. Both pipe and cable seals are divided into fire resistance classes that provide information about the fire resistance duration in minutes.
For the closure of cable or line openings with metallic conductors or for busbars or optical fibres in components, cable penetration seals are required. For the installation of cable seals, the occupancy density as well as the necessary distances to the surrounding components must be observed. It is also important to create the cable seals in such a way that it is easy to change the occupancy density later. To do this, add a reserve area of 40% for subsequent allocations.
In the case of cable penetration seals in particular, the optimal solution for a specific application must be found from many design options. As experts in sealings, we would be happy to make this selection.
Not only the sealing measures, but also their documentation is mandatory. For this purpose, we will hand over a declaration of conformity in the form of a general technical approval (abZ) to the site management of your company. In it we declare that the cable seals meet the requirements of the approval. Building contractors need this declaration for the acceptance according to the contracting rules for award of public works contracts. We also mark the sealing with a sign on which all necessary information is noted.